The Smart 3 Phase AC220V-690V 530kw AC Motor Soft Starter
|FOB Price:||US $90-1,200 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $90-1,200/ Piece|
|Payment Terms:||L/C, D/P|
- Model NO.: CMC-530/3-SX
- Output Type: Triple
- Switch Mode: Phase-Shift Trigger Control
- Voltage of Power Supply: Low Voltage Variable-Frequency Drive
- Nature of DC Power: Voltage-Voltage
- Brand: Xichi
- Transport Package: Carton Package
- Application: Three Phase Transducer
- Principle of Work: Three-Phase Voltage Regulation
- Main Circuit Type: Voltage
- Link of Transformation: AC-AC Variable-Frequency Drive
- Function: Elevator Special
- Trademark: xichi
- Origin: Xi′an
★Multiple start mode
Choiceable current limit start, voltage exponential curve start, voltage linear curve start, current exponential curve start and current liner curve start with optional programmable kick-torque and current limit for each mode. Customer may choose different start mode for various application and start your motor in the best way. More accuracy and smoothness for start and stop due to application of the particular algorithm pattern.
★Dual parameter function
This function allows you to start two motors of different power separately by one CMC-SX with two sets of independent parameters which will reduce your inventory investment.
★Advanced communication function
CMC-SX provides a RS485 interface port, which enables collective control for customer, improves system automatization and reliability. The integrated standard Modbus protocol makes an easy configuration.
★Multiple starting modes
Current-limiting start, ramp current-limiting start and voltage ramp start can meet the site requirements to the maximum extent and realize the best starting effect.
High performance microprocessor conducts digital processing for signals in control system, avoiding the excessive adjustment to analog line so as to obtain the best precision and execution speed.
★Powerful anti-interference performance
All external control signals adopt optoelectronic isolation and are set with different anti-noise levels. The device is applicable for use in special industrial environment.
The unique compact structure is designed to be easily integrated into user's existing system, saving expenses for restructuring of system.
Multiple motor protection functions such as over-current, input/output phase-failure, short circuit of thyristor and overheat protection can guarantee motor soft starter not to be damaged in case of fault or incorrect operation.
Pilot signal coding system composed of 4-digit number display monitors working condition of the system for 24 hours and meanwhile provides quick fault diagnosis.
Conditions Of Usage
|Control Power||AC110V--AC220V±15% 50/60Hz|
|Adaptive Motor||Squirrel-cage three-phase asynchronous motor|
|Start Mode||1) Current-limiting start;|
2) Voltage exponential curve start;
3) Voltage liner curve start;
4) Current exponential curve start;
5) Current liner curve start;
|Stop Mode||1,Soft Stop; 2,Free Stop; 3,Brake Stop|
|Starting Times||It is recommended not to exceed 10 times per hour.|
|Protective Function||1,Over-heat protection for soft starter;|
2,Protection for too long starting time;
3,Input open phase protection;
4,Output open phase protection;
5,Phase error protection;
6,Phase current unbalance;
7,Electrical leakage detecting;
|Cooling Pattern||Natural wind cooling|
|Place to be used||Indoor location with good ventilation free from corrosive gas and conductive dust.|
|Enviroment Condition||Below 2000M. It have to rise the rate power when the altitude is more than 2000M.|
Ambient Temperature -25+45°C
Ambient Humidity 95%(20°C±5°C)
Dust: If too much dust, it will reduce the insulation level of the soft starter, even causes the soft starter does not work.
Brush the dust with clean and dry brush.
Remove dust with compressed air machine.
2. Condensation: If condensation, it will reduce the insulation level of soft starter, even causes the soft starter does not work.
(1) Blow it with a hair dryer or electric stove.
(2) Bring it to power distribution room for dehumidification.
3. Regularly check components' intact. Whether it can work properly.
4. Check soft starter' cooling channel, ensure they are not clogged by dirt and dust.
Before maintenance checking, it has to cut off all power in the line side of soft starter.